(ITEM# 3) (REQ#1602279) MOD-0002 - WR# HQC80192 (THIS REPLCES REQ# 1421013) IMMEDIATE PREPARATORY WORK, ACTUAL WORK AND FOLLOW-ON WORK NEEDED TO ACCOMPLISH NEEDED UTILITY TIE INS FOR THE ANNUAL STEAM OUTAGE ON OR ABOUT JUNE 4, 2010, PER GILBANE PROPOSAL DATED MAY 7, 2010.   THE TOTAL OF THIS MODIFICATION WILL BE SUBTRACTED (ZERO SUM CHANGE) FROM FROM THE PREVIOUSLY NEGOTIATED TOTAL OF $19,254,028 FOR  HHSN263999900408I-HHSN29200069-0000 WHICH IS NOW PLANNED TO BE FUNDED WITH ARRA FUNDING IN LIEU OF R&I.  CAN 8362256 - ORF FY-2010TAS::75 0838::TAS  08003820100DB0CROSS REFERENCE BASE - DESIGN/BUILD WEST UTILITY TUNNEL, BLDG 10 - HQC80192 - LOG#26098 - NATE ADAMS - CT# HHSN263999900408I / HHSN29200069.  CROSS REFERENCE HHSN263999900408I  /  HHSN29200036 FOR SCHEMATIC DESIGN (15%) OF THE BUILDING 10, DESIGN/BUILD WEST VAULT UTILITY TUNNEL, MLP9/BLDG 10 J-WING MEP TUNNEL INFRASTRUCTURE UPGRADE - WR# HQC80192.CAN 8362256 - ORF FY-2010TAS::75 0838::TAS  08003820100DB0BUILDING 10, DESIGN/BUILD WEST VAULT UTILITY TUNNEL, MLP9/BLDG 10 J-WING MEP TUNNEL INFRASTRUCTURE UPGRADE - WR# HQC80192 - SOW FOLLOWS;STATEMENT OF WORKTHE INTEGRATED SERVICE PROVIDER (ISP) SHALL FURNISH ALL LABOR, MATERIALS, SUPERVISION, EQUIPMENT, INSURANCE, TAXES, OVERHEAD, AND ALL OTHER FORMS OF EXPENSE AND SERVICES NECESSARY TO PERFORM ALL PROFESSIONAL DESIGN AND CONSTRUCTION SERVICES STATED HEREIN AND AS STATED IN THE BASE CONTRACT, NO. 292-03-D-0107, TO DESIGN, BUILD, AND OUTFIT A POWER, CHILLED WATER, AND STEAM UTILITY TUNNEL BETWEEN MLP-9 AND J-WING OF BUILDING 10.MLP9/BLDG 10 J-WING MEP TUNNEL INFRASTRUCTURE UPGRADECONTRACT NO.:  292-03-D-0107WORK REQUEST # HQC80192             LOCATION:  NIH, CAMPUS, BETHESDA, MD.PROJECT CONTACT PERSONSCONTRACTING OFFICER (OVERALL AUTHORITY IN ALL CONTRACTUAL MATTERS FOR THIS PROJECT)KENNETH M. ROMANNATIONAL INSTITUTES OF HEALTHOA-ORF, AECCBBUILDING 13, ROOM 2E-489000 ROCKVILLE PIKEBETHESDA, MD 20892-5711TELEPHONE:  301-435-4332PROJECT OFFICER NATHAN ADAMSNATIONAL INSTITUTES OF HEALTHOFFICE OF RESEARCH FACILITIESBUILDING 13, ROOM 210 9000 ROCKVILLE PIKEBETHESDA, MD 20892TELEPHONE: 301.402.7126 TITLE: DESIGN, BUILD, AND OUTFIT WEST UTILITY TUNNEL DATE: NOVEMBER 2, 2009PROJECT OFFICER: NATHAN ADAMSCAN: 0-8362256 (FY 10)THIS STATEMENT OF WORK COVERS THE REQUIREMENTS FOR THE DESIGN AND CONSTRUCTION SERVICES NECESSARY TO DESIGN, CONSTRUCT, AND OUTFIT A UTILITY TUNNEL BETWEEN MLP-9 AND J-WING OF BUILDING 10.BACKGROUND: THE NATIONAL INSTITUTES OF HEALTH (NIH) USES A SYSTEM OF STEAM AND CHILLED WATER PIPES TO DISTRIBUTE STEAM AND CHILLED WATER FROM A CENTRAL GENERATION PLANT TO THE VARIOUS BUILDINGS ON CAMPUS. OVER THE YEARS, SEVERAL SECTIONS OF PIPE AND MANHOLES HAVE NEEDED REPLACEMENT DUE TO AGING INFRASTRUCTURE. THERE IS A PROJECT TO INSTALL MULTIPLE BUS DUCTS FROM MLP-9 TO BUILDING 10. AS PART OF THIS PROJECT, AND TO COORDINATE DESIGNS, IT WOULD BE PRUDENT TO DESIGN THE RELOCATION OF THE STEAM AND CHILLED WATER PIPES WITH THE BUS DUCT DESIGN TO ENSURE THAT THE DESIGN IS SUCH THAT THE TWO PROJECTS CAN BE CONSTRUCTED IN THE MOST EFFICIENT MANNER POSSIBLE. THIS WOULD ALSO AVOID INTERFERENCES, LIMIT EXCAVATION TO A SINGLE OCCURRENCE, AND COORDINATE DESIGN SUCH THAT IF FUTURE REPAIR IS NECESSARY THERE WILL BE MINIMAL OBSTRUCTION.  THERE IS ALSO A PROJECT TO UPGRADE BUILDING 10 MEP INFRASTRUCTURE (MASTER PLAN) TO ALLOW USE OF OLD BLDG 10 PCU'S FOR RESEARCH ACTIVITIES, INCLUDING, BUT NOT LIMITED TO, NCI ANATOMICAL PATHOLOGY RESEARCH.IN ADDITION TO THE AFOREMENTIONED ISSUES, MANHOLE 76 (WHICH HOUSES STEAM AND CHILLED WATER VALVES) IS AT A POINT WHERE FURTHER DETERIORATION WOULD NECESSITATE REPLACEMENT. THIS PROJECT MUST REPLACE THE STEAM AND CHILLED WATER LINES AND RELOCATE THE VALVES TO A DEDICATED UTILITY TUNNEL COMBINED WITH THE ELECTRICAL BUSS DUCTS.  THIS PROJECT MUST ALSO COORDINATE LOCATIONS OF NEW STEAM & CHILLED WA